Medical gas distribution shall be supplied by pipe drops to a single point connection above the unit. All Medical Gas Outlets and piping shall be brazed and tested in accordance with NFPA 99c.
Wire for standard and critical branch power circuits shall be #10 or #12 type THHN stranded copper wire, 600 volt, with heat resistant thermoplastic insulation.
All ground conductors shall be installed in conduit. Where electrical terminations are located inside the flatwall, a grounding bus will be installed for each type of power, and shall be installed as to ensure grounding for the complete power system.
Electrical receptacles shall be Hubbell Hospital Grade 15 or 20 amp, 120 or 277 volt, UL listed and marked Hospital Grade. Simplex, duplex, and (optional) safety receptacles shall be NEMA style 5-15R or 5-20R. Optional locking receptacles shall be simplex type, 20 amp, 120 or 277 volt, color black, and be HUBBELL lock 23000 HG style.
Low voltage data provisions shall be connected to device junction box via conduit. Amico Corporation shall include pull cord extending from service provision to electrical termination point.
Switching shall be HUBBELL Industrial Grade 120 or 277 volt, 15 or 20 amps. Switch type options include SPST, 3-Way or Momentary. Low Voltage Switching will be 0-12 volts, 15 amps unless otherwise noted. Amico Corporation shall furnish, preinstall and wire all switches.
An optional decorative wood valance can be added on and between two flatwall units to complement the room. The wood valance is constructed of particle board with laminate finish, colored to match the flatwall. The integrated light is a 3' (91.44 cm) fluorescent light with two bulbs provide by Amico and provides reading light above the bed.